A release of gasoline from a buried transmission line led to the installation of a groundwater pump and treat system to extract gasoline-impacted groundwater from overburden and fractured dolomite bedrock. Site topography also resulted in surface water ponding above the plume and flooding of interceptor trenches. The treatment system eventually required significant enhancements based on a Feasibility Study (FS) conducted by another firm. Our client was under severe time constraints to meet regulatory deadlines established in a Consent Order from the state environmental regulatory agency.
Geosyntec’s Scope of Services
Geosyntec was retained to design the needed enhancements to the existing treatment system and to perform construction quality assurance (CQA) services during its implementation. Geosyntec began by designing a surface water control system to keep the ponded surface water from infiltrating into the subsurface. We also designed a bedrock trench for groundwater extraction purposes to improve the removal of BTEX compounds and methyl tertiary butyl ether (MTBE) from overburden and the fractured bedrock. Finally, we made design improvements to the existing groundwater treatment system that consisted of an oil/water separator, air stripper, and granular activated carbon. Geosyntec conducted additional aquifer testing in the deep bedrock system to evaluate further enhancements for MTBE removal and prepared all permit modifications for the project.
During the construction of both the surface water control system and the enhancements to the groundwater extraction and treatment systems in challenging winter conditions, Geosyntec provided CQA services to ensure a level of quality that was required by our client, the regulators, and local stakeholders. Optimization of the groundwater extraction and treatment system has reduced system downtime and improved mass removal.
Geosyntec has repeatedly demonstrated technical success throughout the course of this project in several aspects. First, we successfully designed the surface water control system to reduce infiltration into the groundwater extraction system. Second, groundwater levels were maintained at the desired elevations to extract free product. Third, we also improved the groundwater capture zone for the system, including establishment of upward vertical gradients. Notably, we have improved the BTEX/MTBE mass removal efficiency of the groundwater extraction system by 20-fold compared to the previous system. As a result, the groundwater extraction system was able to be turned off approximately five years after the implementation of the groundwater extraction and surface water control improvements. The client estimated Geosyntec’s design and implementation saved them more than ten million dollars by greatly reducing the duration of groundwater extraction at the site. In addition, the client was released from the Consent Order by the state environmental regulatory agency.
Quick QualNo pages found in your document. What is a Quick Qual?
- Location: Midwest U.S.
- Client: Confidential
- Project Practice Areas: Contaminated Sites
- Type of Facility: Transmission Line
- Services Provided: Surface and Groundwater Control System Design; Aquifer Testing; Treatment System Design; Permitting; Construction Quality Assurance; System O&M; Groundwater Monitoring; Regulatory Negotiation
- Type of Work: Mitigation
- Governing Regulation: State and Local